Warehouse storage management 2021-06-20 10:01:24 According to the provisions of the national 'Code of Fire Protection for Building Design(1) In front of the cargo warehouse, a special person should be sent to check and confirm that there are no hidden dangers such as fire before the warehouse. (2) Goods stored in the open air should be sorted, piled, grouped and piled, and necessary fire separation distances should be reserved. The total storage capacity of the yard and the fire distance between buildings must meet the requirements of the building design fire protection code. In general, the floor area of u200bu200beach stack should not be greater than 100 square meters, the spacing between stacks and stacks should not be less than 1 meter, the spacing between stacks and walls should not be less than 0.5 meters, the spacing between stacks and beams and columns should not be less than 0.3 meters, and the width of the main channel should not be less than 2 meters. (3) Goods that are easy to spontaneously combust or decompose in water should be stored in a place with low temperature, well-ventilated and dry air, and special equipment should be installed for regular testing, and temperature and humidity should be strictly controlled: (4) Different types of flammable and explosive The packaging containers of the goods shall be firm and sealed to prevent running, spilling, dripping and leakage. The storage must be divided into compartments and warehouses, and the name, nature and fire extinguishing method of the stored goods must be marked in a conspicuous place. At the same time, offices and rest rooms are not allowed in the warehouse. (5) The used oily cotton yarn, oily gloves and other oil-stained fiber items and combustible packaging should be stored in a safe place and disposed of regularly.